Bitte um Hilfestellung.
Seit einigen Tagen versuche ich das Problem in den Foren sowie im Internet zu lösen.
Ich habe eine USG 4 Pro
2Stk 24 Port Switch
5Stk ACP alles von UNIFI alle auf 2,4 GHZ
Software und Firmware am letzten Stand.
bei Shelly registriert
Yes, Shelly 1 can accept 12V, but it's REGULATED 12V. The power supply in motorhome will vary between 12V and 14V depending on the state of charge of the batteries and Shelly 1 will not like that.
The workaround is to install a DC voltage regulator so…
Yes, you can always accomplish this with calling the API directly, but I'm trying to avoid that. I want to standardize all device communication (not just between Shellies, but also with others like Sonoff) on MQTT.
After more research I think the best way…
I have this issue as well. Even on multiple shelly devices.
Did any of you solve this?
Tried various fw versions.
Using neutral line.
Dimming 6x 5w ikea bulbs.
Funny thing is the device have been running fine for a few months.
I was able to do that, but not with regular dimmers. I used 2-way push button switches (regular 2 way but with a spring installed)
So I click the switch to turn on the lamps, then hold the switch to adjust the brightness. Holding the switch will turn up…
No that won't work, I believe with the Shelly Dimmer 2 you can't have toggle switches on S1 and S2.
S2 I believe is used for dimming in combination with S1. (S1 dim up, S2 dim down)
A simple on off can only be connected to S1 if I recll correctly.
I havent tried the neutral solution myself, but I guess it should look like this:
Would this setup work with the shelly dimmer 2?
1.9.5 has been redrawn, due to problems
It's a very different circuit if you are running neutral.
Instead of the Live in to the 2-way switch at Location 2 I believe it should be the neutral.
Ignore that I just looked at the manual, looks like it can be either neutral or live. Are you…
I just tried your solution (two way switches) but with the neutral wired, and when I tried to toggle my dimmer through the app it broke at my electrical panel.
Edit: Ok I think my issue is I used a L wire from another circuit breaker.
Alternatively if you have 1-way push buttons then this setup should work without neutral. You need to configure the buttons as "One button mode"
I went with the no-neutral and two way switch and works great. Thankfully I had a live wire in both locations which simplified matters alot. Otherwise I would use the push button in both locations.
Here's my two-way switch wiring, with button type "Toggle…
falls es für jemanden nützlich ist, ich aktualisiere die Bibliothek auf https://github.com/bmachuletz/ShellySharp
hin- und wieder.
Für den Shelly 2.5 habe ich bereits einen Event-Listener integriert. Diese löst aus, sobald sich der Status…
First post hope someone can help
I am trying to switch on and off an Air conditioner via the Air cons control panel.
The Data Line incoming only had 5v so i wired an adapter in and have the Shelly Powered
There are separate buttons for on and off so…
I agree and all the product images for the light is kind of deceptive because it looks on the site (if you don't read the specs) that they are sized like "normal" lightbulb but in the produkt images are not representative for the real product.
I have configured a quick action for one of my shelly motion and after a long time searching i found that you can do the setup again under i/o actions but i can not understand what to do if i just want to remove current action i can only configure a new…
Note the last two posts should be a day apart. First one was still sitting the browser and hadn't been submitted.
OK, I have tested numerous other devices operating right next to the access point with no ill effect.
Only the Shelly devices are having a problem with proximity.